These cookies are necessary for the basic functions of the shop.
"Allow all cookies" cookie
"Decline all cookies" cookie
These cookies are used to make the shopping experience even more appealing, for example for the recognition of the visitor.
Statistics & Tracking
Track device being used
Capacitive Voltage Detecting Systems with Relay Contacts, with Partial Discharge Detection, for High Voltage
Item number: 2502134_H009
Item number: 2502134_H009
The CAPDIS-S2_HV (R5) is an integrated Voltage Detecting Systems for checking for absence of... more
Product information "CAPDIS-S2_HV (R5)"
The CAPDIS-S2_HV (R5) is an integrated Voltage Detecting Systems for checking for absence of voltage in high-voltage switchgear in accordance with IEC 62271-213:2021 (or IEC 61243-5) with integrated three-phase continuous indication and Signaling outputs. It also allows detection of partial discharges in the station and its surroundings.
Voltage Detecting Systems VDIS for High Voltage (52 - 480 kV)Testing for absence of voltage in high voltage switchgear according to IEC 61243-5 resp. IEC 62271-213 with integrated three-phase continuous display.
Partial discharge detectionCritical partial discharge levels are detected, shown on the display and output via the relay collective fault signal. The sensitivity of the PD detection is set or also deactivated via a DIP switch on the rear of the device. A socket behind the front flap is available for PD diagnostics.
Maintenance-free due to self-monitoring, fail-safeNo periodic retesting according to IEC 61243-5 or IEC 62271-213 u. BGV A3 required, as the device permanently monitors the response threshold and displays it with a three-stage voltage level indicator (half, full and outlined lightning arrow).
Integrated self-test functionNo external test device is required to test for absence of voltage. Integrated function test by means of test button, according to patent DE 103 04 39 Clear indication of primary voltage present and not present.
Relay outputs and LED displaysFor remote monitoring of voltage states, two signal relays [changeover contacts] are integrated, which are operated with auxiliary voltage. The status of the relays is additionally indicated via LEDs in the front.
Integrated V-interfaceFor further processing of the voltage signals via a smart grid system (e.g. IKI-50, IKI-22) connection via optional Y-cable.
Integrated three-phase measuring pointThe device has a three-phase LRM measuring point for phase comparison, rotating field direction measurement e.g. by means of CAP phase or connection of CAPDIS-M.
No battery requiredVoltage test as well as self-test without battery or auxiliary voltage.
|Product designation||CAPDIS-S2_HV (R5) Capacitive Voltage Detecting Systems with relay contacts | with partial discharge detection| for high voltage|
|Standard||IEC 61243-5, IEC 62271-213|
|Required data for order||Rated operating voltage Un, coupling capacitance C1|
|Intrinsic safety||Device is intrinsically safe|
|Maintenance test||No periodic inspections are necessary for this device|
|Broken lead detection||Can be activated/deactivated via DIP switches|
|Partial discharge detection|
|Controls and display|
|Response time relay||<= 1 s|
|Front display||Monochrome LC display and colored LEDs|
|Dimensions and type of installation|
|Case height x width x depth||48 x 96 x 37 mm|
|Cutout height x width||45 x 92 mm|
|Norm cutout dimensions||DIN IEC 61554:2002-08|
|Installation type||Panel mounting|
|Operating temperature||-25°C ... 55°C|
|Storage temperature||-30°C ... 75°C|
|Voltage level||53..480 kV (High-voltage)|
|Rated frequency||50 Hz, 60 Hz|
|Type of interface||LRM|
|Lifetime||Minimum 22 years (MTBF)|
|Connection of connecting cables||By means of flat plug sleeve 4.8 x 0.8 mm or system plug (order separately)|
|Switching capacity relay||250 VAC, 5 A (resistive load) / 30 VDC, 5 A / 250 VDC 0.3 A (resistive load)|
|Auxiliary power supply||24 - 230 V AC/DC +-10%|
|Power supply||24 - 230 V AC/DC +- 10%; Power input < 1 Watt|
|Power consumption||< 1 W|
|Insulation voltage||2 kV|
|Battery||No battery required|